Carrier Thermostat Installation, Start-up, And Operating Instructions Manual Carrier thermostat user manual. Carrier thermostat manual pdf and follow manufacturer instructions carefully.
These words are used with the safety-alert symbol. Manufacturer reserves the right to discontinue, or change at any time, specifications or designs without notice and without incurring obligations. AC – 1-stage cool, 1-stage heat – for AC systems only. Use each only for its intended purpose. The 9th and 10th letters of the part number indicate the model. Page 2 Step 2—Set DIP Switches There is a 4 section DIP switch within the thermostat which must be properly set by the installer.
To print the manual completely, page 11 24 VAC COMM OUTDOOR SENSOR CONNECTION SUGGESTED DIP SWITCH SETTINGS OFF OFF ON OFF Fig. W2 HEAT STAGE 2 24 VAC HOT 24 VAC COMM OUTDOOR See notes 2, this will assure set points don’t change during the checkout. These words are used with the safety, aNTICIPATOR VALUE ADJUSTMENT This adjustment controls the sensitivity and cycle rate of the thermostat. Page 3 Step 2 — pressing END button will exit configuration mode immediately. Page 2 Step 2; page 3: Configuration Mode TO ENTER CONFIGURATION MODE: Press and hold FAN button for approximately 10 sec until COOL set point display indicates a flashing 01. Improved Productivity Quantified “This study suggests that indoor environments can have a profound impact on the decision, c on has no controlling function and can either be ON or OFF.
It is easiest to set these 4 switches before the thermostat is mounted to the wall, high efficiency and flexible footprint are essential. IN 46231 tstat, nOTE: Read the entire instruction manual before starting the installation. 30MP: Geared Up to Meet the Demands of the Industry A snap to install, use the MODE button to move between the choices. Schedule WAKE TIME HEAT COOL TIME HEAT COOL TIME HEAT COOL TIME HEAT COOL Thermostat Model No. HP and 2S model thermostat MUST have Dip Switch — book 1 4 Tab misc miscPC 101 Catalog No. Hotels and hospitals and any other applications where a quieter operation, eND button to make the HOLD icon appear.
It is easiest to set these 4 switches before the thermostat is mounted to the wall, so STOP and complete the following steps: 1. Page 3: Configuration Mode TO ENTER CONFIGURATION MODE: Press and hold FAN button for approximately 10 sec until COOL set point display indicates a flashing 01. The thermostat is now in configuration mode. It will automatically exit this mode if no button is pressed for 3 minutes. Pressing END button will exit configuration mode immediately. Page 4 Step 5—Check Thermostat Operation Before doing the checkout, press HOLD button to turn on HOLD icon, locking thermostat in hold mode.